When I was working on my second EPC project in Senoro, which was gas processing facility, I read that there are several natural gas quality that shall be complied. In the project, we also had to guarantee that the facilities can process gas from wells so that it met requirement as stated in contract. In this post, I want to share you the quality designation parameters for natural gas. To understand more about this area, please check ISO 13686: Natural Gas – Quality Designation.
This is the forth post of city gas series. Check my previous post about how to calculate city gas flow rate, city gas network part 1, and understanding metering and regulating station. In this post, I want to share you about regulating sector.
Before being distributed to house, gas pressure and gas flow from tapping point will be monitored in metering and regulation station (MRS). After leaving MRS, gas will be distributed via distribution pipeline which is usually MDPE pipe.
In my project we use 63 mm pipe or 90 mm pipe for distribution pipeline.
Gas distribution is usually grouped. Each group covers several houses, which can be as low as 900 houses to 2000 houses. In each group, we installed regulating sector. Read More
In this post, I want to share you typical LNG tank instrumentation. This post is related to my old post: rollover in LNG storage tank. As explained previously, rollover in LNG storage tank begins with stratification which is LNG layer formation due to density differences. To monitor stratification, good and necessary instrumentation should be installed thus prevents rollover. Read More
In previous post, I share you one important part of city gas distribution equipment which is Metering and Regulating Stations (MRS). For review, the function of MRS is to monitor flow rate of gas and to reduce gas pressure thus it meets requirement. Gas pressure is reduced from more than 16 bar to 5-15 bar in MRS. I checked in “City Gas Network Handbook” published by Indonesian Government, maximum pressure of city gas distribution system is 7 bar, although in reality, gas operating pressure is not that high. Read More
This is second post of city gas network series. For the first post, please check “City Gas Flowrate Requirement”.
City gas distribution is one of Indonesia national priority program which purpose is to diversify energy, to reduce energy subsidiary, to provide clean and cheap energy, and as complementary program to convert cerosene into Liquified Petroleum Gas (LPG).
The total installed city gas until now is 56,888 house connection. It will be increased year by year. For example in 2013, the government planned to installed 16,000 connection. Read More
In previous post (typical process flow diagram of small scale LNG regasification facility), I explained that LNG storage tank played important part in the facility. It is used to stored LNG for certain duration (usually in term of round trip). In small scale LNG regasification facilities, vacuum insulated tank is usually used because the capacity if small. But when the capacity is high, LNG flat bottom tank is used.
In this post I want to share you difference and comparison between LNG flat bottom tank and vacuum insulated tank and give some advice what to choose.
Table below shows comparison of flat bottom storage tank and vacuum insulated tank. Read More
Currently I am working on city gas network project in Mojokerto. This is my first experience. You can see in my curriculum vitae what I actually do in this project.
My job is relatively more simpler than what I did in LNG project. I need to prepare four process documents which are:
- City gas flow rate calculation
- Line sizing
- Hydraulic analysis
- Polyethylene pipe thickness calculation
In my third LNG project, I had a chance to meet two different LNG storage tank vendors. One vendor produce vacuum insulated storage tank (pressurized type) and the other one produce flat bottom storage tank (atmospheric type).
During the meeting I got several terms of LNG flat bottom storage tank types, such as single containment tank, double containment tank, and full containment tank. What was that?
In this post I want to share you different types of LNG flat bottom storage tank and its special features. Read More
Until now, I’m still dealing with LNG regasification system. I knew now that I don’t quite understand how to choose regasification method. And I understand that technology is getting better, so you have many options which type of regasification to choose, which one is the best.
I’ve studied several type of vaporizers, such as ambient air vaporizer, both natural draft and forced draft, open rack vaporizer, and intermediate fluid vaporizer, using glycol-water or propane. I had a correspondence with several vendors regarding that vaporizers. However, I haven’t encountered with submerged combustion vaporizer or intermediate fluid vaporizer with Rankine cycle. So, I can’t imagine how those vaporizers really work.
In the past, I remembered I encountered with Indirect Fired Water Bath Heater (personally, this term is really long, I can’t easily remember :D). But the application is not to regasify LNG, but to increase temperature of natural gas. In other word, it is gas post treatment after leaving vaporizer.
In this post, I want to share you summary of everything I learned until now about how to choose correct vaporizer for your condition. And I also want to share you some type of unique vaporizers (for me it is unique). Read More
I think reading BS EN 1160 makes my writing ideas grows. As a follow of of this post (LNG Basics: Understanding Its Typical Properties), I want to share you what I read and browsed about Rollover in LNG Storage Tank.
Rollover in one of physical phenomena explained in BS EN 1160, other than Rapid Phase Transition (RPT) and Boiling Liquid Expanding Vapor Explosion (BLEVE).
Rollover refer to process whereby large quantities of gas can be emitted from an LNG storage tank over a short period of time. How this could happen? Read More